# data[].attributes.body
This conductor failed the tug test. It was pulled from the MCB in the distribution board and upon inspection I noticed the copper has started to snap off.

# data[].attributes.attachment_caption
Sharp edges on the metal tray work, just needs some filing

# data[].attributes.body
In the distribution board the terminations are not doubled over

# data[].attributes.body
Trunking has only been used for some of the wires and not all of them

# data[].attributes.body
Shroud bit loose
Live wire fell out L1 on bottom switch from tug test
No twin and earth for sockets, done in 2.5mm singles
Lighting circuit done wrong (distribution board went to light first not to switch then light)
Finish unfinished tasks

# data[].attributes.body
The wire has been been terminated incorrectly, trapping the insulation which is is a potential fire risk.

# data[].attributes.body
Bare copper showing at the neutral terminal.

# data[].attributes.body
Traywork was slightly wonky

# data[].attributes.body
Too much copper showing at termination of a switch.

# data[].attributes.body
Too much slack on plugs and switches
Switch missing cpc running through it

# data[].attributes.body
These conductors we’re loose and fell out the terminal. It also shows that the earth insulation has been trapped by the screw. There is also to much outer sheathing in the box.

# data[].attributes.body
Great workmanship despite this horrible blunder🤬🤬

# data[].attributes.body
Damaged CPC

# data[].attributes.body
This SWA cable was not properly terminated, upon taking the shroud off the steel all flared out. Quality over quantity all day long. Dominik a better attempt next time please.